|4/2017 - 7|
Five Level Cascaded H-Bridge D-STATCOM using a new Fuzzy and PI Controllers model for Wind Energy SystemsYANMAZ, K. , ALTAS, I. H. , MENGI, O. O.
|Click to see author's profile on SCOPUS, IEEE Xplore, Web of Science|
|Download PDF (4,408 KB) | Citation | Downloads: 170 | Views: 180|
wind energy, flexible AC transmission systems, current control, fuzzy logic, proportional control
power(25), control(17), statcom(11), multilevel(11), voltage(9), wind(8), system(8), inverter(7), turbine(6), systems(6)
Blue keywords are present in both the references section and the paper title.
About this article
Date of Publication: 2017-11-30
Volume 17, Issue 4, Year 2017, On page(s): 49 - 58
ISSN: 1582-7445, e-ISSN: 1844-7600
Digital Object Identifier: 10.4316/AECE.2017.04007
Web of Science Accession Number: 000417674300007
SCOPUS ID: 85035747970
Power quality is one of the important issues in wind energy systems as in all renewable energy systems. Reactive component of current in distribution systems causes negative effects on the network, including power loses, voltage drop, and reduced line capacity. Static Synchronous Compensator (STATCOM) has been used increasingly instead of conventional devices such as switched capacitor groups and Static Var Compensator (SVC) to improve the power quality. Flexible AC Transmission System (FACTS) devices such as STATCOM are also used in power distribution systems and called Distribution STATCOM (D-STATCOM). D-STATCOM is used to improve the power quality in distribution systems as an inverter based device. Fixed parameter conventional PI controllers are usually used to control D-STATCOM devices. D-STATCOM device used in a wind power distribution system has a voltage-controlled inverter structure based on a five-level H-bridge topology. A new indirect current control scheme based on synchronous reference frame theory is proposed to produce gate pulses that are needed for the inverter. A fuzzy adaptive PI controller (FLCM-PI) is designed and used in the control scheme such that the parameters of the PI controller are modified by a fuzzy logic controller (FLC) to adapt the operation for changing conditions. The D-STATCOM topology with the proposed controller is simulated and experimentally tested.
Web of Science® Times Cited: 0
View record in Web of Science® [View]
View Related Records® [View]
SCOPUS® Times Cited: 0
View record in SCOPUS® [Free preview]
There are no citing papers in the CrossRef Cited-by Linking system.
Disclaimer: All information displayed above was retrieved by using remote connections to respective databases. For the best user experience, we update all data by using background processes, and use caches in order to reduce the load on the servers we retrieve the information from. As we have no control on the availability of the database servers and sometimes the Internet connectivity may be affected, we do not guarantee the information is correct or complete. For the most accurate data, please always consult the database sites directly. Some external links require authentication or an institutional subscription.
Web of Science® is a registered trademark of Thomson Reuters, Scopus® is a registered trademark of Elsevier B.V., other product names, company names, brand names, trademarks and logos are the property of their respective owners.
Faculty of Electrical Engineering and Computer Science
Stefan cel Mare University of Suceava, Romania
All rights reserved: Advances in Electrical and Computer Engineering is a registered trademark of the Stefan cel Mare University of Suceava. No part of this publication may be reproduced, stored in a retrieval system, photocopied, recorded or archived, without the written permission from the Editor. When authors submit their papers for publication, they agree that the copyright for their article be transferred to the Faculty of Electrical Engineering and Computer Science, Stefan cel Mare University of Suceava, Romania, if and only if the articles are accepted for publication. The copyright covers the exclusive rights to reproduce and distribute the article, including reprints and translations.
Permission for other use: The copyright owner's consent does not extend to copying for general distribution, for promotion, for creating new works, or for resale. Specific written permission must be obtained from the Editor for such copying. Direct linking to files hosted on this website is strictly prohibited.
Disclaimer: Whilst every effort is made by the publishers and editorial board to see that no inaccurate or misleading data, opinions or statements appear in this journal, they wish to make it clear that all information and opinions formulated in the articles, as well as linguistic accuracy, are the sole responsibility of the author.